Shandong zhangqiu yi tai machinery manufacturing co., LTD
Contact: xin-sheng cheng
The true: 0531-83209474
WeChat ID: 13705411652
Q Q: 2458379166
Mail box: 6411111111 @163.com
Web site: www.zqlcfj.com
Company address: Shandong zhangqiu MingShui hou home park street
1, check before starting the:
(1) check the connection bolt, nut elastic.
(2) check reducer lubrication conditions, make the oil level is at the core of standard oil.
(3) check the belt tension and pulley reverse biased.
(4) check the power supply voltage and frequency.
(5) check if the instrument is normal, if there is any abnormal timely notify the maintenance personnel change.
(6) the main valve on the pipeline, the need to run the fan outlet valve is opened, the other is not running of fan outlet valve in the "closed" state, avoid the over load operation of the fan, the machine is damaged.
2, check the boot:
(1) if you need the fan running "frequency", then only need to put on the electric cabinet fan switch to "power frequency" file, and then press the "start" button, the other fan switch and the inverter switch to "stop", pay attention to in the "start" button before be sure to check the running fan outlet valve is open, press the "start" button of the blower fan are consistent with actual instance.
(2) if you need the fan running "frequency", the switch of the converter to overthrow the "start" button, and then put on the electric cabinet after the blower switch hit the "frequency" file, pay attention to other fan switch in the "stop", before the switch to "frequency" file must check the operation of the fan outlet valve is opened, the "frequency" button of the blower fan are consistent with actual instance.
(3) after the fan running (typically take 1 minute of time), then the closing of the exhaust valve slowly, to avoid the closing too fast, cause instantaneous electric current too big fan motor burn out.
3, in the operation of inspection:
(1) adjust the inlet valve of the contact oxidation pool, make uniform aeration;
(2) the control of dissolved oxygen in 2 ~ 4 mg/L (by dissolved oxygen meter reading).
(3) the early because of the lubricating oil viscosity and have high noise and current situation, run 10 to 20 minutes to go away.
(4) the flow cannot adjust by switch valve. The fan is cubage type compressor, by adjusting the rotational speed to change the flow and shaft power;
(5) in a normally closed state, the switch of pressure for pressure gauge switch can be opened when the pressure is measured.
(6) the same aircraft noise also has difference, because the location of the fan in the machinery room and piping of the differences will cause the noise.
4, shutdown check:
(1) open slowly "vent valve to open."
(2) press the "stop" button on the electric cabinet.